|Home||Energy Physics||Nuclear Power||Electricity||Climate Change||Lighting Control||Contacts||Links|
The FNR Open Steel Lattice (OSL) is a disk shaped open steel lattice assembly that is 15 m diameter X 1.5 m high. The OSL is positioned centrally on the bottom of the primary sodium pool. The functions of the OSL are:
a) To support the fuel assembly;
b) To contain and position the actuators for the movable fuel bundles;
c) To allow cool liquid sodium to flow into the bottom of each fuel bundle;
d) To protect the bottom of the primary liquid sodium pool from long term neutron damage;
e) To provide low friction bearings between the upper surface of the bottom of the primary liquid sodium pool and the lower surface of the OSL such that in a seveere earthquake the fuel assembly and the OSL remain in position while the primary sodium pool walls and floor move with the surrounding ground.
The OSL has a nearly flat bottom surface. The primary sodium pool has a bottom with a nearly flat upper surface. Between these two surfaces is a layer of one inch diameter ball bearings. Thus, there is relatively low friction connection between the OSL and the bottom of the primary liquid sodium pool.
In a severe earthquake the inertia of the OSL, the fuel assembly and the surrounding primary liquid sodium will tend to keep these masses in position while the walls of the primary sodium pool move with the earthquake vibrations. Note that the walls can move horizontally up to 0.8 m relative to the OSL before an impact between the OSL and the intermediate heat exchanger support columns can occur. If these columns fail the relative movement can be up to 1.8 m before the OSL impacts the primary sodium pool wall. That distance is believed to be sufficient to endure public safety during the largest recorded earthquakes.
Provided that all the movable fuel bundles are fully withdrawn the FNR should be safe against a severe earthquake.
Note that the high pressure sodium for the movable fuel bundle actuators must be delivered to the OSL via thin tubes that can safely flex 2 m in any direction when these tubes are fixed 16 m above. Note that in an earthquake these thin tubes are subject to considerable drag forces.
FUEL TUBE BUNDLE MATERIAL AND DIMENSIONS:
The fuel tube bundle frame and shroud are fabricated from HT-9 steel (85% Fe, 12% Cr, 1% Mo, 0% C, 0% Ni).
The height allowances for the octagonal fuel bundle components from bottom to top are: legs (1.5 m), bottom grating (0.1 m), fuel tubes (6 m), lifting point (0.3 m), swelling allowance 0.1 m. Hence the fuel bundle shipping container and the air lock tube must be able to accommodate a fuel bundle with an overall length of 8.0 m.
The present design provides an ideal initial 0.25 inch clearance between a movable fuel bundle and each of the adjacent fixed fuel bundles. With good dimensional tolerance control this clearance should be sufficient to allow reasonable core zone material swelling.
The fixed octagonal fuel bundle maximum outside face to outside face distance is:
23 X (5 / 8) inch = 14.375.0 inches.
The square movable fuel bundle maximum outside face to outside face distance is:
19 X (5 / 8) inch = 11.875 inches.
To prevent overall fuel bundle swelling in the core region in that region the shroud plates are eliminated.
An important issue in earthquake protection is bolting the fixed fuel bundles together to form a rigid matrix. We do not want liquid sodium sloshing back and forth to change the fuel assembly geometry and hence its reactivity.
Note that the open steel lattice near the bottom of the primary liquid sodium pool will thermally expand with increasing surrounding liquid sodium temperature. During normal reactor operation the open steel lattice is likely to be about 120 degrees C cooler than the liquid sodium temperature at the top of the fuel bundle. Hence the differential horizontal width thermal expansion per fuel bundle is approximately:
20 ppm / deg C X 120 deg C X 13.125 inch = 0.0315 inch
The fixed fuel bundle leg sockets must provide sufficient play to accommodate this differential thermal expansion.
OPEN STEEL LATTICE:
The 1.5 m high open steel lattice supports the entire weight of the fuel assembly and stabilizes the hydraulic actuators. This steel lattice provides sufficient distance separation between the fuel bundles and the bottom of the sodium pool to ensure that there is no long term deterioration of the stainless steel pool bottom due to neutron absorption. This open lattice also allows free circulation of liquid sodium beneath the fuel tubes. A 1.2 m long fuel bundle diagonal plate bottom extension maintains separation between each movable fuel bundle and its hydraulic actuator. This separation extends the working life of the hydraulic actuators. The fixed fuel bundle diagonal plate bottom extentions keep the fixed fuel bundles 1.5 m above the open steel lattice to protect that lattice from neutron damage. The sockets mounted on the top of the open steel lattice correctly position the fixed fuel bundles. However, a fixed fuel bundle can be released from socket by removing its 4 top bolts and then lifting the fixed fuel bundle a few inches using the overhead gantry crane.
MECHANICAL RIGIDITY CONSIDERATIONS:
A major issue in fuel bundle design is horizontal mechanical stability and rigidity because the overall fuel bundle height of 8.0 m is much greater than its width (.3016 m or 0.3651 m). Hence, the mechanical design of the fuel bundles is important to ensure that during fabrication, transport, installation and operation the fuel bundles do not bend, warp or otherwise deform. Such bending or warping could potentially cause a jam in the sliding of a mobile square fuel bundle within the surrounding matrix of fixed octagonal bundles.
A fixed octagonal fuel bundle has corner girders which extend down below the fuel tubes to also serve as support legs and attach to the diagonal sheets that provide lower central support and an upper central lifting point. On installation the corner girders of fixed octagonal fuel bundles connect to adjacent fixed octagonal fuel bundles by through bolts at the top of each corner girder and by cast sockets at the bottom of each corner girder. The cast sockets are firmly attached to the open steel support lattice. The cast sockets are tapered at their tops to allow practical blind mating with the fuel bundle supports with +/- 6 mm position error. The axis of the cast sockets lies at 45 degrees to the axis of the fuel bundle grid.
The corner girders of every fixed fuel bundle extend downwards 1.5 m below the bottom of the fuel fuel tube support grating. At the top of the fuel bundle 0.3 m diagonal sheet extensions provide lifting points for fuel bundle installation and removal. Short corner girder upward extensions allow use of bolts for connecting together adjacent fixed octagonal fuel bundles.
The entire weight of the fixed octagonal fuel bundles is supported by the four fuel bundle legs and the reinforced diagonal sheet extensions. These supports extend 1.5 m below the fuel tube bottoms to allow movable fuel bundle travel, to allow liquid sodium to easily flow into the bottom of the fuel bundles and to minimize long term fast neutron damage to the open steel lattice.
In operation each movable fuel bundle's weight is borne by its hydraulic actuator which sets the amount of movable fuel bundle insertion into the matrix of fixed fuel bundles. The movable fuel bundle travel is limited at the bottom by its support length (1.2 m) and the hydraulic cylinder end piece and piston thickness (0.3 m) and height of the steel lattice (1.5 m) and at the top by a hydraulic actuator vent hole.
About 0.3 m of height is dedicated to the fuel bundle gratings and bottom filters.
The hydraulic actuator for a square movable fuel bundle consists of a 1.5 m long hydraulic cylinder 9.75 inch ID, 10.75 inch OD + 9.74 inch OD piston which moves the bottom of a movable fuel bundle support up and down, and is located in the open steel lattice. Each hydraulic actuator has a bottom fitting which mates with the corresponding hydraulic pressure line. The movable fuel bundle bottom support OD matches the hydraulic cylinder ID to keep the movable fuel bundle upright when the movable bundle is fully retracted and there are no surrounding fixed fuel bundles. The support has a bottom taper for smooth insertion into the hydraulic cylinder.
The hydraulic piston has sealing piston rings similar to those in a diesel truck.
The fuel tube spacing within a fuel bundle is maintained using a spiral 20 gauge wire winding on each fuel tube and the diagonal amd shroud plates.
The extent of insertion of a movable fuel bundle into the fixed fuel bundle matrix is determined by the volume of liquid sodium inside the corresponding hydraulic actuator. There is fluid pressure feedback which indicates the approximate movable fuel bundle vertical position due to the changing buoyancy of the indicator tube. The hydraulic fluid feed tube is routed through the open steel lattice. This hydraulic tube must be sufficiently flexible to allow for +/- 2 m earthquake induced movement of the primary sodium pool with respect to the open steel lattice.
In the event of a complete hydraulic cylinder jam a portion of the open steel lattice may have to be removed and replaced. The open steel lattice portions must be engineered to fit through the available airlock(s). These portions are bolted together to maintain their relative positions.
To cause a movable fuel bundle to insert into the fixed fuel bundle matrix liquid sodium at up to 100 psi is injected under the hydraulic piston which gives up to 7466 lb of lifting force to raise the movable fuel bundle and its indicator tube. If the piston attempts to move too high the high pressure liquid sodium behind the piston is released into the primary sodium pool via a vent hole in the hydraulic cylinder side wall. This arrangement provides a certain upper limit on the piston travel. An orifice located on each high pressure sodium feed tube limits the rate at which a movable fuel bundle can be inserted into the matrix of fixed fuel bundles. For normal piston position control an orifice restricted hydraulic drain valve is used. However, note that the movable fuel bundle hydraulic drain valve used for reactor safety shutdown is not orifice restricted.
PASSIVE FUEL BUNDLES:
In order to achieve fuel bundle interchangability the passive fuel bundles are the same size and are mounted in the same manner as the active fuel bundles. However, the passive fuel bundles are supported so that their square bundles are not mobile and will not fall out of the fixed fuel bundle matrix.
HYDRAULIC ACTUATOR COMPONENTS:
There is a 0.15 m high X 9.75 inch OD piston that slides within the 10.75 inch OD X 1.5 m hydraulic cylinder to cause insertion of the square fuel bundle into the octagonal fuel bundle matrix.
Mass = Pi (10.750^2 - 9.759^2) inch^2 / 4 X 1 m X (.0254 m / inch)^2 X 7.874 X 10^3 kg / m^3
= 81.79 kg
Hydraulic cylinder bottom disk:
Mass = Pi (9.750 inch / 2)^2 X 0.5 inch X (.0254 m / inch)^3 X 7.874 X 10^3 kg / m^3
= 4.8168 kg
Hydraulic Cylinder Piston:
Piston Mass = Pi (9.750 inch / 2)^2 X 3 inch ____X (.0254 m / inch)^3 X 7.874 X 10^3 kg / m^3
= 28.91 kg
MAXIMUM COMPONENT SIZE:
Sooner or later some component of the open steel lattice assembly will need replacement. All such components must fit into the heat exchanger airlock. The height from the basement floor to the primary sodium pool deck is 19 m, so that height sets the maximum possible component length. This air lock has to be about 2 m deep to allow for heat exchanger connecting pipe and for the hydraulic piston assemblies. This airlock internal width is limited to about 1.1 m by adjacent heat exchanger radial piping and by the intermediate heat exchanger diameter. This airlock is physically off-set to realize sufficient pool deck floor space for its trap door.
Hence the open steel lattice is fabricated in 30 slices, the longest of which is 7.7 m long X 1.5 m high X 1.0 m wide. For other slices the hight and width are the same but the lengths are shorter. Each slice supports three half rows of fuel bundles. Each slice has its own pressure connections for both movable fuel bundle actuators and for open steel lattice bearing support.
This web page last updated July 12, 2021.
|Home||Energy Physics||Nuclear Power||Electricity||Climate Change||Lighting Control||Contacts||Links|